Views:0 Author:Site Editor Publish Time: 2021-11-15 Origin:Site
The voltage stabilizer has the advantages of novel design, small size, beautiful appearance, low loss, low noise, and impact resistance. If the voltage stabilizer fails, it can be analyzed and repaired from the following aspects.
Here is the content list:
l Failure analysis
l Maintenance introduction
⒈Exceeding the voltage stabilizer range of the voltage stabilizer itself (replace the wide-range voltage stabilizer)
⒉The travel limit switch is broken (replace)
⒊The circuit board is broken (replace)
⒋The servo motor is burned out (replace)
An unexpected trip during work
⒈The total brake capacity selection is small (replace the appropriate capacity air switch)
⒉The air switch is broken (replace)
⒊The surge voltage is too high instantaneously (replace the non-contact high-precision voltage stabilizer)
The inside of the regulator is buzzing loudly
⒈Overloaded with load (reducing the equipment connected afterward)
⒉There is debris inside (remove the debris)
The general maintenance and inspection items of the voltage stabilizer are as follows:
⒈Whether there are still design and installation defects in the voltage stabilizer;
⒉Check whether the load current and operating voltage of the voltage stabilizer are normal;
⒊Check whether the voltage stabilizer has oil leakage, whether the oil level, oil color, and temperature exceed the allowable value. The upper oil temperature of the oil-immersed self-cooling voltage stabilizer is generally below 85℃. Strong oil-air cooling and strong oil-water cooling are stable. The pressure device should be below 75℃;
⒋Check whether the high and low voltage porcelain bushings of the voltage stabilizer are clean, whether there are cracks, breakages, and flashover discharge traces;
⒌Check whether the connection terminals of the voltage stabilizer have poor contact or overheating;
⒍Check whether the operating sound of the voltage stabilizer is normal; there is a uniform humming electromagnetic sound during normal operation. If there is a crackling discharge sound inside, it may be a breakdown of the winding insulation. If there is an uneven electromagnetic sound, it may be iron the core bolts or nuts are loose.
⒎Check whether the hygroscopic agent of the voltage stabilizer has reached a saturated state;
⒏Check whether the throttle valve of the voltage stabilizer is normal, whether the shut-off door leading to the gas relay and the shut-off door of the radiator is in the open state;
⒐Check whether the diaphragm of the explosion-proof tube of the voltage stabilizer is intact, and whether the diaphragm glass is engraved with the word "ten";
⒑ Check whether the cooling device of the voltage stabilizer is operating normally, whether the temperature of the radiating pipe is uniform, and whether there is any blockage of the oil pipe;
⒒ Check whether the housing of the voltage stabilizer is well-grounded;
⒓. Check, whether the relay is full of oil and no gas, exists;
⒔ For outdoor voltage stabilizers focus on checking whether the foundation is good and whether the foundation is sinking. For the poles, check whether the electric poles are firm and whether the wooden poles and pole roots are decayed.
⒕ For indoor voltage stabilizers, focus on checking whether the doors and windows are intact and whether the blind wire gauze is intact;
⒖ Other items that should be checked.
If you want to know the home voltage stabilizer and automatic voltage stabilizer repair method, welcome to consult us.